Ex II 2G Ex d IIC T6 Gb
II 2D Ex tb IIIC T85°C Db, -60°C≤T amb≤+60°C
Certificate: BVI 14 ATEX 0072
Ex d IIC T6 Gb
Ex tb IIIC T85°C Db
Certificate: IECEx EPS 14.0082
IP66 (IP65 with option OPV)
Service: air and non-conductive, noncorrosive gases.
Wetted materials: 302 SS, glass, nickel, silicone rubber and brass.
Accuracy: ±0.25% f.s.* at room temperature *RSS includes nonlinearity, hysteresis and nonrepeatibility.
Stability: ±1% f.s. year
operating and compensated: 0 to 170°F (-18 to 77°C)
storage: -65 to 185°F (-54 to 85°C)
case: -76 to 140°F (-60 to 60°C)*
Pressure limits: 15 psi (100 kPa)
Power requirements: 16 to 32 VDC
Output signal: 4 to 20 mA
Zero adjustment: potentiometer for zero
Max loop resistance: DC 0 to 800 Ohms
Electrical connections: screw-type terminal block.
Mounting orientation: vertical, on a 1.378” (35 mm) DIN rail.
Thermal effects: includes zero and span ±0.01 f.s.°F, 20 to 170°F (-7 to 77°C)
Response time: approximately 10 ms. Additional delay in response time due to flame arrestors; from full scale to 0 up to 90 sec depending on model range.
Material: alluminium (stainless steel optional)
Finishing: texture epoxy coat RAL7038 suitable for installation in harsh environments.
Process connections: 1/8” female NPT brass (stainless steel optional)
Electrical connection: 1/2” NPT F (cable gland non included)
Dimensions: see drawing below
Weight: ab. 5 kg
* Operating ambient temperature is defined also according to the options and pressure instrument choosed.
CAUTION FOR USE ONLY WITH AIR OR COMPATIBLE GASES!
CONTACT FACTORY FOR USE WITH GASES, OTHER THAN AIR AND NITROGEN.
Important notes for installation:
Cables must be fitted through 1/2” NPT cable gland or Atex/IECEX conduit (not supplied with instrument).
Make sure after cabling to close tight cover and cable gland, in order to keep IP66 rating
(IP65 with option OPV, pressure reliev valve).
Open cover only after de-energising instrument.
Attention: check local safety rules and warnings on unit and manual for a correct use